Application: Electric heat-traced stations prevent freezing even in extreme conditions. Thermostat regulated units are heated by self-limiting heat-tracing cable wrapped around internal pipe. Units are intended for cold weather use down to -40°F. See ‘Tempering Valves’ section to ensure tepid water compliance with ANSI Z358.1-2014.
Heating Cable: Self-regulated with external termination guards. Thermostat activates when internal piping temperature falls below 75°F. FM, UL, and CSA approved for Class I, Division 2, Groups B, C, and D.
Electrical System: Unit is fully wired at factory. Junction box and components rated for Class I, Division 2, Groups B, C, and D. Requires 120 VAC single phase power supply.
Jacket/Insulation: UV-resistant orange ABS plastic with polyethylene foam insulation. Jacket sections secured with removable stainless steel screws for easy maintenance.
Shower Head: 10” diameter orange ABS plastic with 20 GPM flow control.
Shower Valve: 1” IPS brass stay-open ball valve. US-made with brass ball and PTFE seals. Includes stainless steel actuating arm and 29” stainless steel pull rod.
Spray Head Assembly: Freeze-resistant with float-off dust covers and internal flow control.
Eyewash Valve: 1/2” IPS brass three-way self-draining stay-open ball valve. US-made with brass ball and PTFE seals. Includes 1/2” NPT port to drain water from spray heads after use.
Pipe And Fittings: Schedule 40 galvanized steel.
Supply: 1-1/4” NPT female bottom inlet.
Sign: ANSI-compliant identification sign.
Quality Assurance: Factory tested prior to shipment. Ships fully assembled and crated.